Murickens group an ISO certified company introduces two trade brand name MG and Flyline products with the aim of power saving, maintains free, competitive price and to save power of state by introducing/promoting solar based home appliances and lights. Commonly we use Offline and Online UPS and now a days peoples are thinking about solar ups. Murickens are very popular in kerala real estate market. We help peoples to buy and sell their properties.
FLYLINE MODULAR DIGITAL HIGH & LOW VOLTAGE PROTECTOR
Flyline Modular digital Over & Under Voltage Protector (FDP) is safe guarding all costly home appliances,cctv,security alarm systems,laboratory equipments,computer etc from lightening and voltage variations due to natural calamities .FDP is an advanced device with latest German Technology.Voltage variation in power supply will cause damage to our home appliances.FDP protecting all appliances from voltage cut off ,low voltage cut off and time delay can be set.All these functions user can set and self healing.The electrical protecting equipments available in the market defects like no outstanding ,the system will not work if earthing is not proper and once it is off .we have to put it on manually.FDP is switching "off" and switching "on" automatically.Even if you are not in the house the FDP is taking care of all appliances,cctv security alarm system etc.FDP is an ideal equipment for located houses of NRI's.The FDP will act if the following occurs.
1.Phase sequence disorder
2.Phase unbalance3. of neutral line.4.Breakage of any line level.5.Over under voltage is any phase line.FDP can be fixed in main distribution board easily
►Rated Power Supply : AC220V 50Hz Operating Voltage: 100-400 V (avoid burning out of electrical appliances under 380 voltage)►Passing Max. Current : 32A,63A. ►Max. Loading Power in Single Phase :7KVA,14KVA ►Over-voltage Action Cut-off Value : AC260±5V, action 0.01second action delay. Recovered Value : AC260±5V. (230-270V adjustable ►Under-voltage Cut-off Value : AC180±5V,0.1 seconds’ action delay. Recovered Value : AC195±5V.(120-210V adjustable).►Time Delay: Start time for First Connection: 15 Second. Delay time is free to set from 5 to 600 seconds after the first time.►Rapid action: The power disconnects the appliances with in 1 sec.►Self Power Consumption : ≤ 3W.►Dimensions(MM) : 84x52x75(LxWxH)
FDP More videos: -Click Here
FDP More images: -Click Here
FDP INSTALLATION VIDEOS: -Click Here
FLYLINE DIGITAL ELECTRIC PROTECTOR VIDEOS:-CLICK HERE
FLYLINE DIGITAL ELECTRIC PROTECTOR MORE IMAGES:-CLICK HERE
1. Rated Power Supply : AC220V 50Hz Operating Voltage: 100-400 V (avoid burning out of electrical appliances under 380 voltage )
2. Passing Max.Current:20A,32A,40A,50A,60A.
3. Max. Loading Power: 4.4KVA, 7KVA, 8.8KVA, 11KVA, 13KVA
4. Over-voltage Action Cut-off Value : AC260±5V, action 0.01second action delay. Recovered Value : AC260±5V. (230-270V adjustable)
5. Under-voltage Cut-off Value : AC180±5V,0.1 seconds’ action delay. Recovered Value : AC195±5V.(120-210V adjustable).
6. Time Delay: Start time for First Connection: 15 Second. Delay time is free to set from 5 to 600 seconds after the first time.
7. Rapid action: The power disconnects the appliances with in 1 sec.
8. Self Power Consumption : ≤ 3W.
9. Dimensions(MM) : 84x52x75(LxWxH)
1.This button : for displaying the voltage (3 phase or 1 phase )Press the button for 10s to switch to single phase voltage indicating.
2. The second button : :delay time setting.Press the button for 10s until the decimal point flashes.Then press button "+"or "-" to set the delay time(5-600s)
3. The third button under voltage value setting. Press the button for 10s then the decimal point of digital panel flashes. Then press “ + ” or “ - ”to set the voltage (120-210V)
4. The fifth button : over voltage value setting. Press the button for 10s, then the decimal point on digital panel will flash. The press “ + ” or “ – ”to set the voltage ( 230-270V)
►Sequence disorder.►Phase unbalance.►Breakage of neutral line.►Breakage of any live line.►Over-voltage of any phase.►Under-Voltage of any phase.
►Relative humidity:≤85%.►Latitude:≤2000m.►No corrosive gas or conductive dust.►Instalation :Vertical mounting on DIN rail
press the forth button ,the last time fault voltage will be displayed in 2 seconds .The lights indicate the fault phase
1.Wire Connection Error
Flashing letters CBA on the board indicates phase sequence error .Change connecting sequence of the live lines to solve this problem.(if OPO appears first and then CBA flashes.Please check if the neutral line and live line where reversely connected.)
2.Phase LossOPO :Lack of neutral line.►:OPA : Lack of Phase A live line.►:OPB Lack of Phase B live line.►:OPC Lack of Phase C live lineThe display board is not lighted:lack of 2 or 3 phases of live lines
3.Phase Imbalance:H-L appears when voltage difference between any two phases is over 35%(>77V)
4.Over Or Under Voltage Protection :H and L on the left ,center and rigt of the indicating board stand for over voltage and under voltage of phase A ,B and C respectively.
Flyline Modular Digital Guard Application Image :-Click Here
Flyline Modular Digital Guard More details :-Click Here
Flyline Digital Voltage Protector Videos: -Click Here
Flyline Modular Digital Guard PDF Download : Click Here
Product Short Informative Videos:- Click here
Product Detailed Informative Videos:- Click here
Useful technical informative videos:- Click here
Green Energy Promotion Videos By MG Group:-Click Now
Watts of some electronic products we use :- Click Here
Flyline Solar power plant installation video of MG Marketing System:- Click Here
Murickens GOVT clients list :- Click Here
Murickes Brouchure :- Click Here
For quick response & order-call ( 91) 09400464444, 09447366779, 08281848484